Basic Gas Line Installation costs will depending on the scale of work and length of piping required. Installation will include all the fittings, connections, regulators, etc. required and COC
With the use of SABS approved regulators, piping and any other equipment required, Gas Experts can offer the safest installation of any Domestic appliance.
For a free, no obligation quotation, send an email to email@example.com
If you already have a Gas line installed but you don't know if it is legal, compare it to the following diagram. Give us a call just to make sure!
A - 1m sideways from Doors and Windows
B - 2m from Drains and Air Vents
C - 3m below windows, unless non combustible roof is installed between containers and windows
D - 1m from property boundary unless boundary is a Fire Wall (if only 2x48kg bottles are installed). If installation is more than 2x48 kg bottles, then it must be more than 3m from boundry.
E - 5m away from a switchable electrical point i.e. plug socket, main power etc. (not a light) to the side of the bottles, or 1.5m above the bottles.
Only Class 1 or 2 copper pipe can be used. NOT what is used in plumbing. Or Approved gas piping.
All copper pipes going through a wall must be sleeved.
Flexible hose may not be more than 2m and may not go through any partition at all (including wood and dry wall).